Electrical tidbit here. Here’s a fix to try for a compressor tripping the breaker.
If your breaker trips shortly after the motor kicks in you might want to try replacing your standard breaker with a ‘high magnetic’ breaker.
A ‘high magnetic’ breaker has a delayed trip to allow for the high current draw when an electric motor starts.
Changed my standard 20A breaker to a high magnetic breaker and my tripping problems went away. They are not sold in home centers or hardware stores. Got mine from Grainger.
Hope this helps.
Most important, what Bill said before you work on the compressor or panel “Make sure the power supply is off!”
New comment? New question? Please add it here along with photos to help others help you with your compressor and equipment problem!